|Material:||CU&AL||Out Sheath Color:||Black Or Customized|
|Core:||1||Cable Mark:||Ink Printing Or Embossing Content Customized|
underground armoured cable,
outdoor armoured electrical cable
18/30KV Medium Voltage Single Core Power Cable (Armoured) , Insulated Cable according to IEC 60502/60228
Single Core Power Cable APPLICATIONS:
The single core cables are designed for distribution of electrical power with nominal voltage Uo/U ranging from 3.8/6.6KV to 19/33KV and frequency 50Hz. They are suitable for installation mostly in power supply stations, indoors and in cable ducts, outdoors, underground and in water as well as for installation on cable trays for industries, switchboards and power stations.
Single Core Power Cable STANDARD:
BS 7835 (LSZH Version)
Noted:Single Core Cables to BS 6622/BS 7835/IEC 60502/VDE 0276
Single Core Power Cable Properties
Special features which we can offer for MV cables:
l Watertight construction (both radial and longitudinal).
l Lead sheath available for options.
l Resistant to heavy vibration.
l Available in long delivery lengths to reduce number of joints.
l Copper or aluminum conductor up to 630mm².
l Metallic sheath and radial moisture barrier made of copper wire or tape.
l Different options for outer PE jackets (LDPE, MDPE & HDPE).
l Different options for LSF, LSZH & FRPVC, being anti-termite or UV resistant as per BS 7835, IEC 60332 etc.
l Strippable insulation screen.
l Metallic screen made of multiple layers of copper tapes or a combination of copper wires and tapes to increase the earth fault current carrying capacity.
l Increased armour conductivity by insertion of hard drawn copper wires in armour.
Single Core Power Cable Construction
medium voltage cables are manufactured using the monosil process. We provide the highly specialized plant, state-of-the-art research facilities and meticulous quality control procedures that are required for the manufacturing of PVC insulated cables for use up to 6KV and XLPE/EPR insulated cables for use at voltages up to 35 KV. The materials are all kept in cleanliness-controlled conditions throughout the production process in order to ensure the absolute homogeneity of the finished insulation materials.
Single Core Power Cable Conductors
Either aluminium or copper conductors are used. Conductors up to 630mm² will be circular, compacted & stranded and shall comply with IEC 60228 class 2. 630mm² conductor will be circular stranded type on which a layer of semi-conducting tape will be applied.
Single Core Power Cable Conductor Screen
This will be an extruded layer of semi-conducting crosslinkable compound applied under simultaneous triple extrusion process over the conductor along with the insulation and the insulation screen. The triple extrusion is a single high precision operation that eliminates the possibility of any contamination between the layers which could create irregularities in the electrical field. By careful material selection and special attention to process parameters, we produce the insulation screen layers with the required degree of stripping force as stipulated by the applicable national or international standard.
This will be an extruded layer of XLPE applied over conductor screen under triple extrusion process along with conductor screen and insulation screen.
This will be a layer of semi-conducting crosslinkable compound which will be applied by triple extrusion process over the insulation.
It will consist of a layer of copper tape applied helically with overlap over insulation screen. Other combinations of metallic screens as per customer ’s requirement can also be provided on request.
In case of three core cables, the three cores are laid up with non-hygroscopic fillers like polypropylene(PP) fillers at interstices and a binder tape is applied with an overlap. These binder tapes can be of PVC or foamed Polyethylene.
Inner Sheath (Bedding) for Armoured Cables
Extruded layer of PVC or PE is applied over the laid up cores for armoured cables. PVC is normally of grade ST2 and PE of grade ST7 as per IEC 60502 Part 2.
In case of armoured cables, the armour is applied helically over inner sheath. For single core cables, it is of aluminium wires and for multicore cables, the armour can be of one among the following options:
a) Galvanized steel wire.
b) Galvanized steel tape.
An extruded layer is applied over the armour in case of armoured cables and over laid up cores in case of unarmoured cables. Outer sheath material can be either PVC, PE, HDPE or MDPE. our
medium voltage cables are normally supplied with red PVC over sheaths complying with BS 6622 or IEC 60502. Other colors may be provided to suit a range of installation considerations such as the effect of UV radiations and differing soil compositions. Anti-termite formulations can also be supplied in addition to graphite-coated over sheaths where on-site testing of the sheath is required.
Fire Performance on Cable Sheaths
Cables can also be supplied with special flame retardant PVC over sheaths to comply with the IEC 60332 standard. We can also supply cables with Low Smoke Halogen Free (LSZH) sheaths according to BS 7211 and BS 6724 standards or other equivalent international standards.
18/30KV Medium Voltage Single Core Power Cable (Amoured)
|Aluminium Wire Armoured Cables|
|Nom. Bedding Thickness||Armour Wire Size||Nom. Sheath Thickness||Approx. Overall Diameter||kg/km|
Why Choose Zhenglan Cable:
Contact Person: sales