CE Certification Fire Resistant Electrical Cable / Single core Heat Resistant Flexible Cable/Rated voltage:450/750V
Contact Person : Linda Yang
Phone Number : +86 16638166831
WhatsApp : +8616638166831
|Minimum Order Quantity :||300 meters||Packaging Details :||Wooden drum, wood and steel drum,as customer's request|
|Delivery Time :||12 days||Payment Terms :||L/C, T/T,|
|Place of Origin:||Henan, China||Brand Name:||Zhenglan cable|
|Certification:||3C; ISO 9001:2015, ISO 14001:2005, OHSAS 18001:2007||Model Number:||0.6/1KV Low Voltage Unarmoured Fire Resistant Power Cable|
|Material:||CU||Application:||Fire Resistant Power Station|
|Insulation:||PVC||Color:||Red Or Black|
|Out Sheath Color:||Black Or Customized||Core:||2|
|Cable Drum Length:||Customized|
fire resistant electrical cable,
fire retardant low smoke cable
0.6/1KV Low Voltage Two cores Power Cable (Unarmoured) , PVC Insulated Cable according to IEC 60502-1
Low Voltage Two cores Power Cable Description:
0.6/1KV PVC Insulated Cables
Low Voltage Two cores Power Cable Construction:
Conductors:Copper or Aluminium conductor, round standed or Shaped, Class 2 to IEC 60228, BS EN 60228. For smaller sizes, a solid round conductor, Class 1 as per IEC 60228, BS EN 60228 can also be supplied upon request.
Noted: Insulation color as per standards or customer requirement.
Low Voltage Two cores Power Cable Application:
These cables are used for electricity supply in low voltage installation system, They are suitable for installation in indoors and outdoors, in cable ducts, under ground, in power and switching stations, local energy distributions, industrial plants, where there is no risk of mechanical damage.
Low Voltage Two cores Power Cable Standard:
Basic design to IEC 60502-1, IEC 60228,BS EN 60228
China: GB/T 12706.2-2008
Other standards such as BS7870,DIN and ICEA upon request
Low Voltage Two cores Power Cable Certificates:
CE, ROHS,KEMA and more others at request
Low Voltage Two cores Power Cable Insulation:
PVC Insulation material and thickness shall be as per IEC 60502-1 and BS 6346. PVC material shall be Type A as per IEC 60502-1 or TI1 as per BS EN 50363.PVC Insulation material as per SASO 1694 rated for 85°C continuous operation is also available upon special request.
Colour Code Colour Code (1):
1 Core: Red or Black; 2 Cores: Red, Black; 3 Cores: Red, Yellow, Blue; 4 Cores: Red, Yellow, Blue, Black; 5 Cores: Red, Yellow, Blue, Black, Green; Above 5 Cores: Black Cores with White numerals
Assembly /Inner Sheath:
Two, Three or Four insulated conductors are laid-up together with non-hygroscopic fillers and the assembly is bedded with an extruded layer of PVC. In case of non- armoured cables, this layer may be omitted
Armour: Aluminum/Galvanized Steel Wires applied helically over the bedding as per IEC 60502 or as per BS 5467, BS 6346. Single core cables shall be Aluminium wire armour. Aluminum/Steel Tapes applied helically over the bedding of multi-core cables as per IEC 60502.
Outer Sheath: Outer sheath shall be of Extruded PVC Type ST2 as per IEC 60502-1 or Type 9 as BS 6346/5467.Special type of PVC sheathing material such as Fire Retardant PVC, Anti-Termite PVC, Anti-Rodent PVC, Sunlight resistant PVC, Oil Resistant PVC are available on special request. Also, special sheathing materials such as LLDPE, MDPE, HDPE, LSF, CPE are available on request.
Fire Performance of Cable Sheaths: Cables can be supplied with special flame retardant PVC outer sheath to comply with the flame test requirements of IEC 60332-3-22, IEC 60332-3-23 and IEC 60332-3-24, can also supply cables with Low Smoke Halogen Free (LSHF) material according to IEC 60502-1, BS 7211, BS 6724 or other equivalent standards.
Two cores (unarmoured)
Diameter of Conductor
Why Choose Zhenglan Cable: