|Material:||99.99% Oxygen Free Copper||Type:||PVC Insulated|
|Application:||For Home Usage||Conductor Type:||Stranded|
heat resistant flexible cable,
fire resistant electrical cable
Suitable for surface wiring indoor or outdoor.
Core number: 2core, 3core
Conductor: Solid or Stranded Annealed copper/ aluminum
Insulation: PVC insulation
Outer sheath: PVC sheath.
Rated voltage: 300/500V
Test voltage: 2000V
Max working temperature: 70°C
Mounting temperature: 0°C-+40°C
Minimum bending radius:
For cable with diameter below 25mm, allowed bending
radius should not be less than 4D;
For cable with diameter above and including 25mm,
allowed bending radius should not be less than 6D;
Standard: IEC227-4 or JB/T8734.2-2016
Packing: 100m per roll (per coil or plastic reel, as your request)
Remarks: Flame retardant, fire resistance (adopt mica tape), low smoking and Halogen free, or other property are available.
ZR cable (flame retardant cable) is the kind of cable with PVC insulation built mixed with fire prevention additive to make it have the capability of preventing or retarding flame spread during combustion.
There are 3 grades of fire prevention available which are
Grade A It is the highest level of flame retardancy. That is, the insulation material, filling rope, fastening (inner cushion) belt/layer and sheath material used in cables are all flame retardant materials.
Grade B Except the insulation material, all other materials are flame retardant.
Grade C Only the sheath material is flame retardant
NH cable(fire resistant cable) is the kind of cable built with a layer of mica tape. Even if the plastic skin is burnt out, refractory layer will help not cause short circuit. When wiring, cut off the refractory layer at the wire head.
LSZH,LSOH,LS0H,LSFH or OHLS cable(Low smoke zero halogen cable)is cable with insulation or outer sheath built using low smoke zero halogen free material to help reduce toxic and corrosive gases produced during combustion.
Termite-proof cable is the cable built with insulation or outer sheath mixed with a kind of materials to prevent termite biting the cable.
|Nom. Cross Section Area (mm²)||Approx O.D mm||Thickness of insulation||Thickness of sheath||20℃max. Conductor resistance (Ω/km)||70℃min. Insulation resistance(mΩ/km)|
Contact Person: sales